|SPRINGWATER LODGE - Inspection Report|
|Facility Type||1 (DWQ)|
|Inspection date||May 01, 2019|
|Violations: A summary of the violations found during the inspection are listed below.|
|Code||Description / Observation / Corrective Action|
|316|| Source unprotected and subject to contamination|
Corrective Action: Reseal and remove the ponding water along the well head.
|322|| Emergency Response Plan|
Corrective Action: P)lease update your Emergency Response Plan and submit a copy to our office.
|Routine inspection conducted today of a water system serving a restaurant and four cottages. Water system is currently on a boil water advisory. A new she d has been installed around the reservoir and pump. 2018 Annual Report has been received by our office. Residual free chlorine was measured to be 0.9 ppm. Operator is to conducted a chlorine residual test daily, please provide an appropriate test kit and log all results. Sampling frequency for bacteriological analysis is to be conducted twice a month.|