|Inspection conducted of source (Money Lake and seepage intake), reservoir and pump house/treatment room. Due to upgrades (filter media replacement, addition of ultraviolet and plant optimization), the water system has been able to maintain turbidity levels of < 1 Nephelometric Turbidity Unit (ntu) (therefore is no longer on any public notice). You are currently considered in compliance with your permit conditions which are:
Adhere to sampling program (Turbidity, algae toxin, chlorine residual).
Quarterly measure disinfection byproducts (note one quarter was missed, but staff will continue this monitoring.
Submit implementation plan for the BC treatment objectives. Proposal received on December 11, 2018. Awaiting Public Health Engineers response prior to official Island Health response.|